HLS - Heat Limit Switch
Heat limit Switch HLS-1100 for use with HOM - Combustion Air Damper
The Heat limit switch is placed in-line with the source of 24v Power to the motor of the damper.(usually between “R” on the appliance and #5(blue wire) of the HOM - Combustion Air Damper ) using regular thermostat wire.
color wiring diagram #1A with Combustion Air Damper and Furnace
color wiring diagram #1B Domestic Hot Water alone.
The Heat limit switch is normally closed but opens when it reaches 130 F cutting the power to the damper and causing the damper to drop open.
After it has cooled back down to 115 F the switch returns to the closed position and restores power to the motor causing the damper to also close.
The Heat limit Switch can be used in conjunction with a regular appliance attached to the Hoyme HOM - Combustion Air Damper (pictured below) without interfering with it’s normal operation.
Last Updated (Thursday, 27 October 2016 15:02)